PRODUCTION COMPRESSOR UPDATES AS OF: 02/09/2015 STATION RUNNING Armbrust OFF Arnold OFF Belknap #2 Creekside OFF Egry YES Gibson OFF Girty #1, #4 Latrobe OFF Mendon OFF Merwin OFF Redbank OFF Roaring Run OFF Shady Plain OFF Valley OFF #1 is not needed. Reassembly is almost complete. Need to set oil tank & install bearing temp sensor. Work will resume on reassembly. Approx 1 week of work is needed. #2, #3 are not needed. Low suction Unit is down with lubricator sensor problem. Will be on-line as soon as possible. Not needed. The entire station is down today for piping revisions & orifice plate inspections. #1 & #4 will be back on later today. #5 is still down for repairs – waiting on exhaust header. PEOPLES GAS EGC STATIONS Limestone Fisher Village Atwood Crooked Creek Shoemaker Creighton #2 YES YES YES YES YES YES Unit #1 is down to control the BTU level. OTHER NOTES: 1. The temporary compressor at Valley is decommissioned as of Monday 2/9. The operating permit expired and unit #3 will be ready soon. 2. Repairs are in progress for the Creekside compressor crankshaft replacement. Reassembly is almost complete. 3. We are waiting for an exhaust header for Valley #5. Ignition upgrade is in progress while the unit is down. Pigging Schedule Pipeline Pig Type Date Description Pipeline Construction Schedule Pipeline Date Description Line / System Down-Rating Schedule Line/System MAOP Regulator Set Pt Time Please be advised Peoples Natural Gas has posted a “Meter Tap Process” document and “Meter Tap Request” form on the Gathering Website under “Guidelines and Procedures”. Please refer to them for future tap requests.
© Copyright 2021